Vacuum degasser can efficiently operate in all closed water circulation system. Its working principle is to put the part of the water cycle system fluid in vacuum environment, then the free gas and dissolved gas in the liquid will be released. Later, this part gas that has been degassing treatment, with absorbent liquid will be note in the water closed-circuit circulation system for circulation. They may absorb the free gas and dissolved gas in the system, in order to balance again. After several times of the process, the water cycle system of free gas and dissolved gas would be removed.
To know the applications of vacuum degasser , we must know the working process of the vacuum degasser
Vacuum degasser can run automatically according to the process of the user preset degassing and the degassing process can be divided into two phases: 1) the water phase: liquid of the system goes into the tank, the gas contained in the liquid will be released, and through the take off the top of the tank automatic vent valve to separate with the system. 2) Vacuum stage: they all gathered at the top of the tank and are discharged through the automatic vent valve. The Water electromagnetic valve will open again; a new liquid will go into the tank. Those treated by the degassing, absorbent liquid will be note back into the system to participate in the circulation, and absorb the gas in the system.
To know the applications of vacuum degasser, we must know the operating conditions
Vacuum degasser is suitable for the water circulation system or water - glycol (40%) mixture system.If it used in other media system may lead to unpredictable damage, we will not undertake any responsibility for this the influence. Please according to the technical parameters in instructions listed to operate vacuum degasser.
To know the applications of vacuum degasser, we must know the security
1. We need installation and maintenance of equipment by a professional.2. Before operation, in order to ensure the safety, please disconnect the power supply and water pressure.3. There are heating component inside the body, please start while it is cool.
To know the applications of vacuum degasser, we must know the installation requirements
1.Please put the instrument in ventilated dry place.2. Equipment should connect to 380 v / 50 to 60 Hz power supply. 3. Please confirm the machine is equipped with the appropriate constant pressure system, water goes in and out the pipe of the vacuum degasser will cause the system pressure fluctuated. There must be equipped with overpressure protection valve in the system, in order to prevent the system pressure gets too high.
Installation and fixed
We proposed to make the equipment installed the lowest temperature of the system (only for heating systems), this is good to the removal of dissolved gas. When installing vacuum degasser, it is important to note that control panel should face the outside, to make it easy to operate. Equipment installation should be in accordance with the operation of local norms. In principle, the vacuum degasser can be installed in anywhere of the machine.